TO REORDER REFER TO B/M # F.O.
Inspect the Airfin Cooler to insure that the cooling coil has not been painted, sprayed with oil, or covered with dirt or dust. Insure that there are no obstructions on the top, bottom, and sides.
Apply power momentarily to the motor on the Model 625 FC to check for rotation. If the rotation is in the wrong direction, rewire the motor.
Open the pump suction valve and fill the system with product. Crack the vent valve in the hot product line and vent all air from the system.
Check all fittings for leaks and make required adjustments. Do not tighten fittings excessively.
Apply power to the motor on the Model 625 FC and start the pump, for the 625 NC model start the pump.
The Airfin Cooler is relatively maintenance free. To insure maximum heat transfer efficiency, keep the cooling coils dry and free of dirt and dust. Periodically, clean the cooling coil by blowing air or steam through the protective shroud.
All Flowserve Corporation, Flow Solutions Division, products must be installed in accordance with Flowserve installation instructions. Failing to do so or attempting to change or modify Flowserve products will void Flowserve’s limited warranty. Flowserve’s limited warranty is described fully in Flowserve’s Standard Terms and Conditions of Sale. Flowserve makes no warranty of merchantability or fitness for a particular purpose and in no event shall Flowserve be liable for consequential or incidental damages.
Argentina Villa Martelli
Australia Marayong NSW
Phone 31-165-581400 Fax 31-165-552622
Phone 54-11-4709-6800 Fax 54-11-4709-7072
Phone 61-2-8822-7100 Fax 61-2-9679-7511
Primary Worldwide Flow Solutions Division Locations
Phone 269-381-2650 Phone 780-463-7958 Phone 416-292-2877
Flow Solutions Division
Licensees, authorized agents, and affiliated companies located worldwide
United States Kalamazoo, MI
Canada Scarborough, Ontario
Singapore Mexico Phone 65-6-8465100 Tlaxcala
Brazil Sao Paulo
Phone 52-2-461-6791 Phone 55-11-4066-8600
Printed in U.S.A.
ISO 9000 Certified
REV 02/03 USA