h.Low pressure sensor alarm
i.High pressure switch alarm
j.Condensate overflow alarm
k.Hi/low voltage alarm
l.Fan “ON/AUTO” position of space thermostat as specified above
p.Fan “ON/AUTO” command
q.Fault reset command
r.Itemized fault code revealing reason for specific shutdown fault (any one of 7)
This option also provides the upgraded 75VA control transformer with load side short circuit and overload protection via a built in circuit breaker.
Climate Master shall warranty equipment for a period of 12 months from start up or 18 months from shipping (which ever occurs first).
FIELD INSTALLED OPTIONS
All units 120000 BTUH (35 kW) and below shall be connected with hoses. The hoses shall be 2 feet (61cm) long, braided stainless steel; fire rated hoses complete with adapters. Only fire rated hoses will be accepted.
The following valves are available and will be shipped loose:
a.Ball valve; bronze material, standard port full flow design, FPT connections.
b.Ball valve with memory stop and PT port.
c.“Y” strainer with blowdown valve; bronze material, FPT connections.
d.Motorized water valve; slow acting, 24v, FPT connections.