2009 Wildwood Water Utility Specifications
The Integral Hydrant Storz nozzle is installed on new hydrants during assembly.
The HIHS meets or exceeds the requirements of AWWA C502 regarding material and pressure testing. A Storz spanner wrench is required for cap removal.
The Storz nozzle shall have a brass metal face seal and hard anodized aluminum Storz ramps and lugs. The aluminum’s finish shall be hardcoat anodized to Mil-A-8625f, Type 3, and dark gray. The adapter shall be made of forged or extruded 6061-T6 aluminum.
The blind cap shall have hard anodized aluminum Storz ramps and lugs; made of forged or extruded 606J-T6 aluminum. The center cap shall be equipped with a suction seal. The cap shall be connected to the adapter or the hydrant with a
O.125” vinyl coated aircraft cable. The high torque cap requires a Storz spanner wrench for removal. Once installed, the Integral Hydrant Storz with cap extends less than 2" front the hydrant nozzle.