XAD Unified Access Control DVR
⑥ The system test shall be witnessed by the authority having jurisdiction. Any deficiencies noted during the testing must be corrected.
d. A letter of certification shall be provided to indicate that the tests have been performed, and all devices are operational.
PART 4 – COMPATIBLE PRODUCTS
ITDC ACCESS CONTROL DEVICE (CONTROLLER BOARD & FIELD PANEL)
Complete distributed processing for any decision-making.
Control up to 4 readers per loop.
Maximum registration of user is 20,000 users and 25,900 transactions.
Shall be interfaced with 26bit Wiegand and 4/8 bit burst from the reader (PIN Pad)
Access verifications for all cards performed at controller.
Linking of Input and output is done locally at controller.
Status LED for each Input and each Output.
Controller polled LED.
Separate communication received and transmitted LEDs.
Self diagnostic LED.
Loaded redundant 7 Amp battery back-up for four hours full system operation including locks and accessories during the emergency AC power failure. Once the AC power is restored, automatic charging circuit on the power supply be on.
Controller that reports to PC any loss of DC power and low battery as separate alarms with