FLOATING FOUNTAIN DETAIL SPECIFICATIONS (cont.)
ELECTRICAL CONTROL PANEL COMPONENTS DESCRIPTION
Electrical enclosure shall be NEMA 3R type, gray in color. Panel shall be both lock and mount capable.
GFCI breaker shall provide overload and short circuit protection, combined with Class A ground fault protection.
Control breaker shall provide overload protection and be capable of disconnecting all incoming electricity from the control panel.
Motor contactor shall provide a means for disconnection of all motor leads. It shall be a magnetic, across the line starter type.
Overload assembly shall provide overload protection by means of a bi-metalic overload relay. It is adjustable over the listed full load amperage draw of the motor. It shall have a visual trip indicator, test button and manual/automatic reset modes.
Timer shall be a single pole type, rated at 120 Volts, 20 Amps, capable of a timing cycle, in 30 minute increments up to 24 hours.
SAFETY TESTING CONTROL PANEL The electrical control panel shall be tested and approved as a complete unit
inspected and listed by Underwriters Laboratories, Inc. under Category 508: Industrial Control Panels and Category 778: Submersible Aerators and Aerating Fountain Pump Systems.
ACCEPTABLE MANUFACTURER This fountain’s electrical control panel, as specified in Section 3.0, shall be manufactured by AQUAMASTER FOUNTAINS AND AERATORS, 16024 CTH X, Kiel, WI 53042, (800) 693-3144 or approved equal.
INSTALLATION The electrical control panel must be installed in accordance with the installation
instructions, in compliance This should be done by
with all local and National Electrical Code requirements.
installation instructions, will product warranty and may
substitution for items in this system, unless allowed by void the Underwriters Laboratories Listing and will void
also create a hazardous the installation and follow
installation. Read the instructions them carefully throughout.
ELECTRICAL CONTROL PANEL WARRANTY All electrical panels and their components have a 1 year warranty.