MD ANDERSON Project No. XX-XXXX
MD ANDERSON PROJECT NAME
A/E Project No.
Month, 00, 0000
NFPA 262 - Standard Method of Test for Flame Travel and Smoke of Wires and Cables for Use in Air-Handling Spaces.
SMACNA ‑ HVAC Duct Construction Standards ‑ Metal and Flexible.
UL 900 ‑ Test Performance of Air Filter Units.
ANSI/ASHRAE/IESNA Standard 90.1 – Energy Standard for Buildings Except Low Rise Residential Buildings.
Manufacturer: Regularly engaged in production of components that issues complete catalog data on total product and has at least five (5) years of manufacturing experience for the product specified.
Performance Ratings: Conform to ARI Standards; bear ARI 430 certified rating seal. If unit is not ARI 430 rated, unit shall be tested in accordance with the standards to establish acceptability.
Sound Ratings: Test air handling unit in accordance with AMCA 300 (ASHRAE 68) and ARI 260 Guidelines.
Air Coils: Certify capacities, pressure drops, and selection procedures in accordance with ARI 410.
Base performance on sea level conditions, unless otherwise scheduled.
Provide complete unit including components designed to operate within range of 35 degrees F to 135 degrees F ambient temperature, 20 to 70 percent relative humidity in conditioned mechanical rooms and 100 percent relative humidity in unconditioned mechanical rooms.
The Contract Documents are based on the equipment scheduled. Contractor is advised that the use of equipment other than that scheduled may directly affect and require coordination with (but not limited to) the following items:
Mechanical room sizes and building structural conditions, with required clearances.
Electrical starter/disconnect switch, wire and conduit sizes; electrical clearances as per NEC.
Ductwork and piping layouts and return air opening sizes and locations.
Plumbing floor drain location.
Units shall fit into the space available with adequate clearances meeting manufacturer’s requirements for service and as determined by the Engineer. Submitted units, which do not meet these criteria, shall be rejected. The Contractor shall not assume that all of the manufacturers listed as acceptable manufacturers will provide a unit that will fit in the space allocated for the unit(s).
Product Data Record Documents:
The University of Texas
CUSTOM AIR HANDLING UNITS WITH FAN ARRAY SYSTEMS
MD Anderson Cancer Center
23 73 24
2 of 4