MD ANDERSON Project No. XX-XXXX
MD ANDERSON PROJECT NAME
A/E Project No.
Month, 00, 0000
Provide literature that indicates dimensions, weights, capacities, ratings, fan performance, gages and finishes of materials, electrical characteristics and connection requirements. Refer to detailed list of submittal data in this Section.
Provide data of filter media, filter performance data, filter assembly, and filter frames as tested and certified per ASHRAE 52.2 and UL-900 class 1.
Provide fan curves with specified operating point clearly plotted, as tested and certified per AMCA standards. Ratings to include system effects. Bare fan ratings will not satisfy this requirement, but shall be submitted for comparison purposes. All fan data shall be generated from specified testing. The fan array shall compare favorably with the scheduled data listed in the Drawings. Hagen's Line plots on fan curves shall be provided for fans operating in parallel, to prove that fans will not be operating in the unstable region.
Submit sound power level data for both fan outlet and casing radiation at rated capacity, as tested and certified per AMCA and ARI 260 Standards. Sound power level ratings shall comply with AMCA Standard 301 "Method for Calculating Fan Sound Ratings From Laboratory Test Data," and shall be the result of tests made in accordance with AMCA Standard 300, “Test Code for Sound Rating”. Fans shall be licensed to bear the AMCA Certified Sound Ratings Seal The Unit(s) shall be finally configured so as not to exceed sound levels are specifically scheduled in the Contract Documents.
Provide data on all coils as tested and certified per ARI standards.
Submit electrical requirements for power supply wiring including wiring diagrams for interlock and control wiring, clearly indicating factory‑installed and field‑installed wiring.
All electrical power, lighting, control, sensor, and pressure taps, and TAB access ports are to be noted on the submittal Drawings.
Wiring shall have smoke and flammability rating of 25/50 or better per test method of NFPA 262.
Note each deviation and reason for the deviation on the shop drawing submittal.
Operation and Maintenance Data:
Include instructions for filter replacement, motor and drive replacement, spare parts lists and wiring diagrams.
Provide Operating and Maintenance (O&M) Manuals for air handling units.
Manufacturer's Instructions: Provide Start-up information and maintenance required prior to Start-up. Coordinate with Division 01, 20, and 26 Commissioning Specifications.
DELIVERY, STORAGE and HANDLING
Deliver, store, protect and handle products to the Project Site under provisions of Division 01 and Division 20.
Accept products on site in factory-fabricated protective containers, with factory-installed shipping skids and lifting lugs. Inspect for damage.
The University of Texas
CUSTOM AIR HANDLING UNITS WITH FAN ARRAY SYSTEMS
MD Anderson Cancer Center
23 73 24
3 of 4