MD ANDERSON Project No. XX-XXXX
MD ANDERSON PROJECT NAME
A/E Project No.
Month, 00, 0000
Store in clean dry place and protect from weather and construction traffic. Handle carefully to avoid damage to components, enclosures, and finish.
Protect openings in casing and seal them with plastic wrap to keep out dirt and debris. Protect coils from entry of dirt and debris with pipe caps or plugs.
The manufacturer shall provide one spare fan motor for each nominal horsepower provided in the fan arrays on the Project.
schedules on drawings
In general, all capacities of equipment and motor and starter characteristics are shown in schedules on the Drawings. Reference shall be made to the schedules for such information. The capacities shown are minimum capacities. Variations in the capacities of the scheduled equipment supplied under this contract will be permitted only with the written direction of the Engineer and Owner.
Insofar as is possible, all items of the same type (i.e., coils, fans, etc.) shall be by the same manufacturer.
Where installation instructions are not included in the Contract Documents, the manufacturer’s instructions shall be followed.
Motor and wheel diameters scheduled on the Drawings are the maximum. If a larger wheel diameter or horsepower is required, note each deviation and reason for the deviation on the shop drawing submittal.
PART 2 -
All materials shall meet or exceed all applicable referenced standards, federal, state and local requirements, and conform to codes and ordinances of authorities having jurisdiction.
Provide all necessary and required tags and decals to aid in the service or indicate caution areas.
Provide complete unit with segments as indicated on Drawings and in this Specification or as required for unit operation in accordance with performance requirements specified herein. Refer to filter Specification Section for filter requirements.
Configuration: Fabricate with fan array and coil sections plus accessories as indicated on the Drawings, including but not limited to:
Applicable pre-filter and final filter sections.
Cooling coil section.
The University of Texas
CUSTOM AIR HANDLING UNITS WITH FAN ARRAY SYSTEMS
MD Anderson Cancer Center
23 73 24
4 of 4