National Partitions, Inc. 10300 Goldenfern Lane, Knoxville, TN 37931
PHONE: 865-670-2100: FAX: 865-670-2200; WEBSITE: www.n-p.com
© Copyright 2009, Authorized use is strictly limited to parties writing specifications for National Partitions projects.
1.Capacity: 7 wire system utilizing three 110 volt 20 amps circuits.
2.Conduit: 1/2 inch diameter flexible BX cable.
3.Wiring: 12 gage, THHN Type, stranded copper.
4.Connectors: Male and female directional type ensuring system is assembled correctly.
5.Provide separate runs to breaker panel for 220 volt circuits serving air conditioners and other equipment.
6.Maximum cable run without junction box connector: 50 feet.
***** Include the following paragraph if outlets, switches, junction boxes, and rigid conduit are being provided as part of prefabricated room but wiring and electrical connections will be responsibility of licensed electrician. *****
F.Electrical wiring system: Provide UL listed outlets and switches with junction boxes, 1/2 inch rigid conduit, couplings, and 90 degree elbows that extend into ceiling plenum. Conduit for light fixtures and all wiring and electrical connections shall be provided by others [as part of Section 16100 - Wiring Methods].
A.Coordinate provision of prefabricated wall panel system with:
1.Concrete slabs specified in Section 03300 - Cast-in-Place Concrete to ensure proper support for wall panels.
2.[Section 03400 Precast Concrete] [Section 05120 - Structural Steel] [Section 13125 - Pre-Engineered Building]: Roof system for attachment and bracing of wall panels.
3.Section 16100 - Wiring Methods to ensure proper wiring and connection of system electrical components to building power supply.
B.Coordinate provision of wall panel system with other construction to ensure that access for delivery of components and storage and staging area is sufficient.
***** Edit this article to include only components and systems being used for prefabricated room. *****
PREFABRICATED ROOMS [Using ]13031-F - 14