National Partitions, Inc. 10300 Goldenfern Lane, Knoxville, TN 37931
PHONE: 865-670-2100: FAX: 865-670-2200; WEBSITE: www.n-p.com
© Copyright 2009, Authorized use is strictly limited to parties writing specifications for National Partitions projects.
A.Erect prefabricated room system in accordance with manufacturer's instructions and approved shop drawings.
B.Do not cut or alter components during installation except as directed by manufacturer's written installation instructions. Do not install bent, dented, or scratched panels and components. Remove and replace components damaged during installation.
C.Layout partition plan on floor with chalk lines according to Drawings and approved shop drawings. Indicate door and window locations.
D.Base channel: Cut pieces to size allowing 1/4 inch corner gaps and 40 inches openings for standard door assemblies. Anchor channel to floor in accordance with manufacturer's instructions.
E.Posts: Loosely assembly two-piece posts. Bolt in structural inserts were required. Install required electrical components in posts.
F.Wall panels: Starting at room corner, construct walls by inserting panels into base channel. Clamp vertical panel edges by tightening post bolts. Temporarily brace wall panels as work progresses.
G.Trim: Snap-in post feature strips on both side of posts to conceal bolts. At room corners bolt together inside and outside trim pieces.
H.Door and window units: Install in same manner as wall panels.
I.Top support member: Fit to wall panels and rigidly attach to roof structure as detailed on approved shop drawings.
***** Include the following paragraphs if suspended ceiling is being provided. *****
J.Ceiling: Attach perimeter wall angle to wall panels. Space main tees at 48 inches and suspend with wire hangers at 48 inches. Space cross tees at 24 inches and attach to main tees. Place ceiling panels in suspension grid. Exercise care not to soil or damage panels.
K.Modular wiring system: Fasten flexible conduit and junction boxes to underside of roof deck. Connect wiring from outlets and switches and extend to breaker panel.
L.Light fixtures: Place at locations indicated on Drawings and approved shop drawings. Support fixtures from roof deck, not ceiling suspension grid. Plug in modular electrical wiring.
3.3TESTING AND ADJUSTING
PREFABRICATED ROOMS [Using ]13031-F - 15