Vent the dryer directly to the outside and install an exterior cap. Use rigid aluminum piping with all
joints properly secured.
Remove old boiler and haul from job site. Install high efficiency, 85% plus AFUE gas boiler. Heating
Systems shall be rooms and other
designed and balanced or adjusted spaces with a heating capacity to
to provide for the distribution of heat to all habitable
maintain a temperature of at least
68° F when the
temperature is -10° F. Contractors shall be responsible for any new gas line for this installation. All equipment shall be installed in accordance with Mechanical Code as approved by the City of Cedar Rapids and inspected by
or electrical wiring required the most currently adopted a City Mechanical Inspector
prior to acceptance.
SEWER/WATER LINE REPLACEMENT
Install a new 1" water supply line from the house to the stopbox or sewer line from house to City main. Secure all required permits. Include a survey to determine the full extent of work including depth of excavation, replacement of paving and sidewalk and all new lines required. Make minimum cut for required excavation, including replacement of all material damaged or removed in the process of sewer/water line replacement. Replacement or patching material shall match existing finish/quality. All work shall comply with all applicable codes. Back fill with clean fill dirt, free from stones or concrete.
Tamp each 10" layer. Finish grade and seed as applicable.
Disconnect old hot water heater and haul from job site. Install a new 40-gallon gas-fired or electric, standard efficiency hot water heater, AUI type, glass lined. Must be UPC approved with at least a 5-yr Warranty on the tank and a one-year warrant on the gas valve. Gas water heater (up to 60 gallons) shall have ≥0.62 EF (energy factor) and electric water heater ≥0.93 EF. Direct-fired heaters shall be provided with a pressure and temperature relief valve. Include a lever gas shut off valve on the gas line. Heater to
be vented and the flue to be of sufficient height to have proper draft.
1002a. Pressure Relief Valve: Install a pressure-temperature relief valve on the water heater - 150 lb. Pressure and 210 degrees. Use ¾" inlet and outlet pipes for relief valve.
1002b. Discharge Pipe: Install a discharge pipe on the water heater. Use ¾" copper or galvanized pipe within 6" of floor.
Install piping and a lever handle gas shut off valve for a water heater, furnace, stove, dryer, or boiler.
Install a new stool. Remove existing fixtures from job site including all piping that cannot be reused when installing new work. Type to be vitreous china white, floor fastened, reinforce floor structurally for new fixtures as necessary with a minimum 1.6 gallons per flush or better. Install to code. Install a water
supply shut-off if none exists. Must be UPC approved. Quality and price to be mid-range.
\\citycr.local\sharedocs\PublicWorks\HSG\Housing Rehab\Specs-Codes\General Specifications.doc