Install wood front, vanity cabinet of the width specified and 21" deep. Cabinet bodies will be ⅜" thick with matching wood grained vinyl laminated to particle board. Cabinet fronts will be ¾" hardwood. Doorframes will be ¾" hardwood and a veneered center panel. Door hinges will be self-closing. Doors will have a reverse bevel for easy opening. Exterior wood surfaces will be stained, sealed, sanded, and
finished with scratch resistant, heat-cured Alkyd-Urea finish. Quality and price to be mid-range.
CULTURED MARBLE VANITY TOP
Install a cultured marble top on the vanity with an integral oval bowl. Top will be 22" deep, ¾" thick with an integral back splash. Top will be drilled for 4" center faucet and for pop-up drain assembly.
Glue top to vanity with silicone, or construction adhesive. Caulk perimeter as needed.
Restore existing faucets to a watertight condition. Replace stems and seats as needed. Any replacement handles shall conform to original style as closely as possible. Prevent tool scarring or damaging fixture.
NEW FAUCET / SHOWER HEAD
Install kitchen sink and/or lavatory faucets. New unit must cover all openings in the present sink, be securely fastened and watertight. Install a supply shut-off if none exists. Must be UPC approved. Quality and price to be mid-range. 2.0 gallons per minute (GPM) or better for kitchen 1.5 GPM or better for
bathroom. Newly installed shower heads must be 1.75 GPM or better.
Install chrome plated bath accessories unless other material specified. Paper Holder and Soap Dish will be recessed. Towel bar shall be either 24" or 30" in length. Shower/bath shall have a grab bar. Properly
secure all fixtures.
Remove and discard old sink and install a double-bowl stainless steel kitchen sink. Sink should be self- rimming, 20 gauge machine-buffed stainless steel. Minimum size shall be 33" by 22". Sink should have
a nickel content of at least 18.8%. Quality and price to be mid-range.
CLOTHES WASHER SUPPLY AND DRAIN
Install water supply and waste piping for an automatic clothes washer. Supply lines will be ½" copper or aqua-pex with a hose bib for hot & cold water. Connect the drain line to the sewer line using at least 2" PVC or ABS sch. 40 plastic, including a trap and proper vent. Any new waste piping will be installed to
CLOTHES WASHER DRAIN ONLY
Install a washing machine drain on the sewer line of at least 2" PVC or ABS piping including a P-trap
and a proper vent; install to code.
WATER SUPPLY LINES
Install all new copper or aqua-pex hot and cold water supply lines with ball valves before and after the meter. Use ¾" pipe from the water meter to the water heater, and ¾" from the water heater to the first hot water branch. All other piping ½" size. Install valves on any second story risers and a cold water ball
valve on the water heater. Shut off valves should be put in place for each faucet or toilet.
DRAIN, WASTE & VENT
Any new waste piping will be of sufficient size according to local plumbing code. Plastic piping to be
\\citycr.local\sharedocs\PublicWorks\HSG\Housing Rehab\Specs-Codes\General Specifications.doc