AUTOMATIC FIRE DETECTION AND ALARM SERVICE
Type (Circle One)
Detectors are installed in all areas, rooms, and spaces as defined in Standard NFPA 72 or NFPA 72E (National Fire Alarm Code) Chapter 5.
Same code requirements as total coverage but protection is only provided for specifically defined area(s) of the protected property. In addition selected coverage may include smoke detection at control units. Must describe details in Comments and Clarifications Section.
Deviations from Total or Selected Area Coverage. Protection provided is less then required by the code in some way. Number of devices and locations shall be specified. Must describe details in System Deviations Section.
Smoke Detectors _____
SPRINKLER SYSTEM WATERFLOW ALARM AND SUPERVISORY SERVICE Note: If all sprinkler risers and water shutoff valves are not supervised, show in deviations section.
Type of System: Quantity
Waterflow Switches (Includes water pressure type)
_______ Sprinkler Valve Supervisory Switches
Other Supervisory Services: Quantity
____Water Pressure Devices
Quantity ____Air Pressure Devices
Quantity ____ Fire Pump Power Devices
Water temp Devices
Room Temp Devices
Pump Running Devices
____Water Level Devices Suppression System) Other Monitored Suppression Systems (ie - Hood ____ _____________________________________________________
© 2012 UL LLC
3 – Revised 05/21/2007
UL Form No. CS-ASD-FAS