DESIGN DEVELOPMENT 2 (DD2)
HEATING, VENTILATING, AND AIR CONDITIONING
l.Provide updated 1:50 (¼”) scale typical mechanical equipment room plans by incorporating previous comments.
m.Provide updated controls, flow and control diagrams.
n.Provide sound/acoustic analysis to ensure compliance with the HVAC Design Manual.
o.Provide demolition drawings indicating scope of work for demolition.
p.Show phasing plans.
q.Show outside chilled and condenser water piping. Show how the pipes will be laid.
r.Show scope of work for ECC, its planned capabilities, and point schedule.
s.Submit several sample specification sections of VA Master Specifications edited with pencil to reflect scope of work of the project. Provide a list of all sections that will be required for the project.
Check compliance by the designer requirements stated in the applicable VA, HVAC Design Manual.
Check smoke and fire protection, and other life safety provisions in the design:
Compliance with VA National CAD Standard Application Guide and applicable National CAD Standard modules.