CONSTRUCTION DOCUMENTS 1 (CD1)
HEATING, VENTILATING, AND AIR CONDITIONING REVIEW
Check whether the A/E submission is in compliance with PG-18-15.
Summary of PG-18-15, A/E submission requirements for the designers:
a.Provide complete and final calculations of all HVAC equipment and systems.
b.Submit sound analysis of various systems and steps taken to ensure compliance with the noise criteria.
c.Complete coordination with other disciplines by providing revised information developed since the last submission.
d.Submit 100 % complete 1:100 (1/8”) scale all HVAC floor plans. Separate floor plans for ductwork and piping, unless waived by VA.
e.Submit 100% complete 1:50 (¼”) scale all mechanical equipment room floor plans with minimum two cross sections at right angles to each other.
f.Show all roof-mounted equipment on roof plans.
g.Provide 100% complete drawings of the outside chilled and condenser water distribution with profiles, sections, and details etc. Show existing utilities through actual inspection at the site and discussions with the medical center.
h.Provide 100% complete automatic temperature control drawings including point schedules for all trades, a riser diagram showing locations of ECC, and field data gathering panels. Show actual location of ECC and peripherals on floor plans.
i.Provide 100% complete HVAC demolition drawings showing clearly the extent of demolition work.
j.Submit HVAC original VA Master Specification drafts marked-up showing the editing for the project. Ensure the specification sections represent accurate coordination between drawings and specifications.