SCHEMATIC 1 (S1)
HEATING, VENTILATING, AND AIR CONDITIONING REVIEW
Check if the A/E submission is in compliance with PG-18-15.
Summary of PG-18-15 A/E submission requirements for the designers:
a.Provide estimated heating and cooling loads based on floor area.
b.Coordinate estimated preliminary steam demand with steam generation designer.
c.Investigate condition and available capacity of existing utilities.
d.Provide description of tentative zoning.
e.Select three different applicable systems for life cycle cost analysis.
f.Provide a list of energy conservation measures to be used in design, and life cycle cost analysis.
Check compliance by the designer, requirements stated in the applicable VA, HVAC Design Manual.
Compliance with VA National CAD Standard Application Guide and applicable National CAD Standard modules.